|Home||» Products||» Generator Auto Start Auto Stop Unit With Remote||» Generator Auto Start|
Generator Auto Start
Backed by our rich industry experience, we are betrothed in offering an extensive assortment of Generator Auto Start that automatically starts the generator in the absence of main supply. Manufactured using superior quality basic components and avant-grade technology, offered product is widely appreciated for its use in commercial and residential sectors. Available in 96mmx96mmx110mm plastic body in a range of 5kva to 600kva, we offer this Generator Auto Start as per its application requirements in pocket friendly price.
Hassle free operation
The Microcontroller/microprocessor based automatic start cum stop unit with battery charger is designed to suit the necessary requirements of customer.
Housed in 96mm x96mm x110mm plastic body ready to be mount in the pane. Available from 5 kva to 600 kva
GSU-2 is suitable for the all types of generators
Indications- Auto,Start,Ignition,Stop,Fail to Start,Main,Generator,Full Charged
Buttons- Manual Start Push, Auto/Manual Selection Switch, Manual Stop/Reset Push
Diesel engine starts automatically after the absence of main supply in 5 sec. Four more starting impulses if the generator does not start in first crank.
Diesel engine set stops automatically after the resumption of all three phases with a delay time of 30 seconds. In case of single phase input all three phases can be looped.
The equipment can be operated in both Auto and Manual mode according to desired output from a unlimited distance with a wired remote provided with the unit. The generator can also be started manually by remote in maual mode.
Generator can be stopped any time either in the absence of mains in manual mode.
Working of Buttons
Manual Start push is used to start the generator manual in manual mode.
Auto/Manual selection switch is used to change the working status of unit.
Manual Stop push has 2 types of working.
To stop the engine manually when the unit is in manual mode.
To reset the unit in case of fail to start condition.
Working of Remote
To change the auto/manual mode
To start and stop the generator manually.
Note: When the unit is in manual mode the generator will stop automatically after the resumption of main supply